28 September 2021
What is the hot and neutral on the coil terminals for CAD50BL?Product Line:
Tesys D IEC Style RelaysCause:
Determine if relay will work for a specific application. Resolution:
Yes, the DC coil is polarity sensitive - A1 is positive and A2 is negative.