Some customers that are familiar with CT wiring for the PM800 do not know there is a wiring difference for the PM200/PM700 for Three-Phase 3-wire Power Systems when using 2 CTs.
For 3-wire, three-phase systems with 2 CTs, connect terminal S2 = X2 of CT1 to the I2+ terminal of the PM200/PM700 instead of the I1- (on the PM800). The PM200/700s firmware use the inverse of the residual current that goes into the I1-, I2- and I3- to know the actual value of current for the third phase. This is not a calculation. It is rather an actual value. By using N-1 CTs in power systems, you can know the actual current value of N phases.
Left: PM200/700 CT Wiring Right: PM800 CT Wiring
Legacy KB System (APS) Data: RESL201198 V2.0, Originally authored by MaTh on 01/29/2010, Last Edited by MaTh on 01/29/2010
Related ranges: PM800 series, PM700 series, PM200 series