If the load which the CM2000 is monitoring losses voltage on any ONE phase, the CM2000 has the ability to alarm on this. The specific alarm is Voltage Loss (Alarm #31), which is an alarm that will become active when any ONE phase drops below the user-defined pickup value. The alarm will NOT become active is all three phases drop below the pickup value.
This specific alarm can be associated with the operation of a relay output on a IOM, if installed.
Note: If the meter losses control power, there is no ability to signal the Voltage Loss alarm unless the CM2 Ride-Through Module is installed.
Note: The same applies for subsequent Circuit Monitor models and PM800 series meters. These meters however have no ride-through module option.
Legacy KB System (APS) Data: RESL185240 V2.0, Originally authored by KBAdPM on 06/27/2007, Last Edited by MaTh on 10/16/2010
Related ranges: CM2000 series