User wants to change the logging interval for Powerlogic meters(CM4000, CM3000, PM800, and/or PM600)
CM4000, CM3000, PM800, and/or PM600
ION Enterprise 6.x
Struxtureware Power Monitoring (SPM) 7.0.x
Power Management Expert 7.x or 8.x
Meter configuration using ION6.0, SPM, or PME
ION Enterprise, SPM or PME software does not have the capability to change the logging interval for the onboard log files
The onboard logging interval can be changed using ION setup software. However, ION Enterprise, StruxureWare Power Monitoring 7.0.x and Power Monitoring Expert 7.2.x or 8.x will not extract Data logs from the meter with an interval at or less than 1 minute interval. A Work around is to create data recorders in the VIP which can log data from the Powerlogic meters at intervals of 1 minute or less. Consider the size and complexity of the VIP and system before such configuration.