PME8 Alarm Web Configuration does not show digital inputs or Alarms created from digital inputs do not populate within Web Applications
Power Monitoring Expert 7.x.x
StruxureWare Power Monitoring Expert 8.x
SQL Server Management Studio
The DI needs to map to a measurement that PME can resolve.
*Warning: Irreparable database damage can occur. This procedure should only be performed by users familiar with SQL Server Management Studio. Databases should be backed up prior to performing this procedure.*
The following query returns all the quantities being logged, including the ones in VIP.
SELECT s.Name SOURCE_NAME, r.Label RECORDER_NAME, c.Label CHANNEL_NAME, q.Name QUANTITY_NAME
FROM Source s INNER JOIN Recorder r
ON s.ID = R.SourceID INNER JOIN Channel c
ON r.ID = c.RecorderID INNER JOIN Quantity q
ON c.QuantityID = q.ID
order by s.Name, r.Label, c.Label
Below is a sample of the result set: