Need to setup a input to take a signal from a WAGES meter
CM4000 Series and PM800 Series, System Manager Software (SMS)
Application monitoring data produced by a WAGES meter.
Information needed before beginning setup
1. What WAGES quantity is associated with each analog input on the PL device (i.e. Analog Input 1 is associated with Water Flow Rate (gal/min) from a water meter).
2. The register numbers in the PL device that are associated with the analog inputs (i.e. An analog card in the C01 position of an IOX on a CM4000 would have a base register of 5320 and the Present Scaled Value would be found in Base +26 (reg. 5346)).
3. The lower and upper limits of the WAGES quantity that corresponds to the analog input (i.e. 0 gal/min equals 4mA and 5000 gal/min equals 20mA).