The following table provides power supply information for the Compact controller.
|Power supply voltage
||Rated power voltage; 100 to 240 vac.
Allowable range; 85 to 264 vac.
Failure - depends on quantity of used inputs and output points. Generally, failure is detected when voltage drops below 85 vac, stopping operation to prevent malfunction.
NOTE: Momentary power interruption for 20 ms or less at 100 to 240 vac is not recognized as a failure.
|Inrush current flow at power-up
||TWDLCAA10DRF and TWDLCAA16DRF 35 Amp maximum
TWDLCAA24DRF 40 Amps maximum
|Power supply wiring
||UL1015 AWG22 (0.64 mm) or UL1007 AWG18 (1.02mm) Make the power supply wiring as short as possible.
||UL1007 AWG16 (1.30 mm) Do not connect ground wire in common with ground wore of motor EQUIPMENT.
Note: The Twido is obsolete and has been replaced with the M221, for more information on this contact your local distributor or Schneider Electric sales.