To determine the heat dissipation of a Magelis XBT-GT5230 based on the VA rating of the unit.
-1 Watt equals to 3.412 BTU/Hr.
-Power Factor of the Magelis XBT-GT5230 is almost one. But for heat dissipation calculation we will use 0.8
XBT-GT5230 Power Consumption: 26VA
To calculate the heat dissipation you need to consider the type of load you are dealing with. Typically if you have a capacitive or inductive load, you would need to know the power factor (PF) to convert to Watts. :
Watts = VA * PF
VA = Watts/PF
VA = 26/0.8 = 32
32 Watts is about 110 BTU/hr.
Therefore the heat dissipation on a Magelis XBT-GT5230 is 110 BTU/hr. Please choose an electrical enclosure accordingly.
Legacy KB System (APS) Data: RESL199025 V1.0, Originally authored by MiMe on 05/28/2009, Last Edited by MiMe on 05/28/2009
Related ranges: Magelis XBT G