Quantum 140CPS11100 power supply not powering up out of box.
No power at initial power up .
The Quantum 140CPS11100 power supply that has a PV 01 or higher require a jumper on pins 3 and 4 on the terminal strip for 115 VAC operations. If this jumper is not installed, it will be set for 220 VAC operations. Any power supply with a PV less than 1 did not require the jumpers.
Note: The Quantum line is obsolete 12/1/2018 and the recommended replacement is the M580 with the x80 I/O, for further information on this contact your local distributor.