If the green led stays lit on the ACE9xx module that means there is a comms wiring issue. For normal working conditions, the green light would be:
a) turned off when Stand-By i.e. Commubnication frame to SCADA
b) flickering when communicating to SCADA
In order to fix the wiring issue, verify:
a) That the module is not grounded more than once. Often, the shield is exposed and grounded unnecessarily with the clamp, which is located below the terminals. Make sure that the shield isn't exposed and touching this clamp.
b) That the RS485 terminals are wired correctly. Here are the wiring diagrams for 2-wire and 4-wire communication:
For 2 wires:
Warning: L+ connects to L- and vise-versa when communicating to a powerlogic or third-party device on the same daisy chain!!!!
For 4 wire:
Date Created: March 4, 2008
Last Revised: September 11, 2008
Original Author: JJ
All content © 1992-2008 Schneider Electric
Legacy KB System (APS) Data: RESL192741 V1.0, Originally authored by PhHa on 09/12/2008, Last Edited by PhHa on 09/12/2008
Related ranges: ACE 9XX