Effects of interruptions of the DC power supply. (CEI60255-11)
The effects are determined for an interruption with a duration chosen in the following list and declared by the manufacturer : 2 _ 5 _10 _ 20 _ 50 _ 100 _ 200 ms
The interruption must be sudden, i.e.the auxiliary power supply must vary from 0 to the rated value and the opposite .
The relay must not change erroneously its output status when the power supply value is applied or cancelled.
Fugitive cancellings Sepam 1000+ S20: 10ms.
Fugitive cancellings Sepam 1000+ S40: 20ms.
Fugitive cancellings Sepam Series 80: 100ms
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 20, 40, and 80
All content © 1992-2008 Schneider Electric
Legacy KB System (APS) Data: RESL166865 V2.0, Originally authored by FrKr on 06/18/2008, Last Edited by DaMi on 06/18/2008
Related ranges: Sepam series 40, Sepam series 20