No, the changing of settings remotely is not password protected.
To modify protection settings remotely in Sepam 1000+ through the Modbus communication link, no passwords are required.
The remote setting feature can be inhibited in each Sepam 1000+ (it's one of the parameters of the General settings)
A controled access to this function have to be programmed in the SCADA system.
The remote setting feature on Sepam 2000 is based on the same principle.
Re-published to revised security level: 17 June 2008 by DRM
Applies To: Sepam 1000+ (Sepam Series 20 and Sepam Series 40)
Original Author: FK
All content © 1992-2008 Schneider Electric
Legacy KB System (APS) Data: RESL166694 V2.0, Originally authored by FrKr on 06/18/2008, Last Edited by DaMi on 06/18/2008
Related ranges: Sepam series 40, Sepam series 20