Conext XW+ Series Inverters - W95 Equalize Abort
Unit is faulting during equalization and aborts the equalize process due to dropped transfer, unit displays a W95.
Solar Inverters, XW/SW series
On-Grid & Off-Grid Systems
This unit is faulting because the AC source is lost. This can also occur if the conductors are undersized for distance, creating voltage drop.
This could also happen if you are using a generator that is not correctly size for the system causing the generator to over load.
Wait until AC input (utility grid) returns to in-tolerance condition, if this doesn't happen it may be necessary to lower the AC input voltage lower limit (Advanced Settings>AC Settings). If Generator is undersized try a different source.