Needs to run a 3 phase motor with 1 phase input voltage.
Cusotmer only has single phase input power but needs to run a 3 phase motor.
Several of our drives have been tested and approved to accept single phase input power to run 3 phase motors.
Drives must be derated to handle the increased current on the input bridge and increased ripple or noise on the DC Bus.
In some cases input line reactors may be required or may allow higher SSCR ratings.
Consult the appropriate Quick Start Guide Annex. These documents also provide fuse and circuit breaker information.
NOTE- product was discontinued in 2016 (Variable Torque applications):http://www.schneider-electric.us/en/download/document/S1B86981/
(Constant Torque applications):http://www.schneider-electric.com/en/download/document/S1B86988/
NOTE - product to be discontinued in 2017 (Constant or Variable Troque applications):http://www.schneider-electric.us/en/download/document/S1B16328/
NOTE - product to be discontinued in 2017 (Constant or Variable Troque applications) :http://www.schneider-electric.com/ww/en/download/document/S1B39941?showAsIframe=true
(Constant or Variable Torque applications): http://www.schneider-electric.com/en/download/document/NVE21777/
(Constant or Variable Torque applications): http://www.schneider-electric.com/en/download/document/S1A58684/
The ATV212 is not capable of supporting single phase input applications.
For any other application requirements consult following 3rd party website (Bonitron):
Only recommended on single phase for pump application (Altivar Process Drive) : https://www.schneider-electric.com/en/download/document/EAV64300/