Powerpact H, J and L frame testing Ground fault, trip test, from the display with Micrologic 6.2A and 6.2E, 6.3A and 6.2E trip units.
Powerpact H, J and L frame
Micrologic 6.2A and E, 6.3A and E trip units
Electronic trip unit user guide 48940-312-01, Rev. 02, 01/2012, page 19.
Ground fault test instructions: Press "mode" button until marker is above the "1/A". Then press the arrow key until marker is above the ground symbol. Press "ok/test" button and the word "test" will be on the display. Press ok/test again to trip the breaker. After breaker trips, press ok twice to reset display. Trip unit must be powered up by enough load, or have external 24Vdc, or have test equipment plugged into the trip unit so you can see the display.
The following notes are taken from the Micrologic 5 and 6 Electronic trip unit user guide 48940-312-01, Rev. 02, 01/2012, page 19. Access the ground-fault protection test function by pressing OK. The tESt pictogram appears and the OK pictogram blinks. Prompt the ground-fault protection test by pressing OK. The circuit breaker trips. The ground-fault protection trip screen is displayed. Acknowledge the ground-fault trip screen by pressing OK. The Reset OK pictogram blinks. Confirm by pressing OK again The confirmation OK displays for 2 seconds.