What are the ranges of the Micrologic 5.0P ground fault alarm pick up and delay?
Microligic 5.0P, 6.0P, 5.0H and 6.0H
Trip units that go on Powerpact P, R; and Masterpact NW and NT
Programming the GF alarm pick up values
Pickup: 0.1 x In to In (In = Sensor size). Floor is 120 amps and Ceiling is 1200 amps, +/- 15%.
Delay: 1 to 10 seconds, -20%, +0%
Drop out: 0.1 x In to Pickup. Floor is 120 amps and Ceiling is Pickup. (Drop out cannot be set higher than Pickup.), ±15%
Dropout Delay: 1 – 10 sec., -20%, +0%