How do you activate the ground fault protection feature on a Masterpact or Powerpact breaker with a 6.0 A Trip unit?
Micrologic, Powerpact, Masterpact
Products sold in North America
Need to remove ground fault from breaker with a LSIG trip functions.
The ground fault cannot be deactivated. The trip unit needs to be replaced to an unit without LSIG trip functions like S143A (5.0A).
CTA-ID : 2030439