QO and Homeline
AFI and AFCI
Electrical Distribution Equipment
No. So-called AFCI ``testers`` are on the market, but they are not UL listed for testing the function of an AFI circuit breaker. UL 1436 refers to them as ``indicators`` rather than testers, and Square D does not endorse them or recommend their use. They are subject to error in the form of giving a false negative result.
The UL approved method of testing an AFCI circuit breaker is to press the push-to-test button when installed in an energized load center or panel. This test injects a signal into the AFCI sensor that looks like an arc to the AFCI. A properly functioning AFCI will trip when the test button is pushed.
Paragraph 31.8.1 of the UL 1436 standard requires the AFCI Indicator markings or instructions to effectively state that the test button on the AFCI circuit breaker demonstrates proper operation.