How to connect the 4 Pole RCCB in 240V AC Single phase network.
To use the 4 Pole RCCB in 240V AC single phase network, connect the Neutral at N and Phase at terminal 1 of the RCCB.
Confirm the functionality of the RCCB with the help of the Test Push Button. The RCCB should trip when the Test Push Button is pressed.
Connection Diagram for Single Phase attached.