How can I achieve maximum redundancy with my Hot Standby/SCADA system?
To protect against media and Ethernet device failure, consider the following:
1. Redundant Monitor Pro SCADA servers at v7.2 or higher.
2. Mesh Ethernet network using Rapid Spanning Tree protocol on ConneXium 499NxS27100 Ethernet switches
3. Or, ConneXium self-healing Ethernet Ring on the 499NxSx7100 Ethernet switches
4. Redundant Hot Standby PLC's with Quantum 140NOE771x1 modules connected to separate ConneXium switches
Note: Shown are dual Ethernet adapters in the SCADA servers. 2 or more adapters can be bound to a single IP address for adapters that support such a feature. Intel adapters support such a feature known as 'NIC Teaming'.
This will allow for PLC, SCADA server, Ethernet switch, and Ethernet media failure and continue operating.
Legacy KB System (APS) Data: RESL173847 V1.0, Originally authored by on , Last Edited by on
Related ranges: Modicon Quantum